Application: Combination WideArea™ eye/face wash and shower
safety station. Four GS-Plus™ spray-type outlet heads deliver a flood of water over a wide area of coverage for complete rinsing of eyes and face.
Shower Head: 10" diameter orange ABS plastic.
Shower Valve: 1" IPS chrome plated brass stay-open ball valve. Valve is US-made with chrome plated brass ball and Teflon® seals. Furnished with stainless steel actuating arm and 29" stainless steel pull rod.
Spray Head Assembly: Four GS-Plus™ spray heads. Each head has a "flip top" dust cover, internal flow control and filter to remove impurities from the water flow.
Eye/Face Wash Bowl: 11½" diameter. Bowl is stainless steel (08G1909) or orange ABS plastic (08G1909P).
Eye/Face Wash Valve: ½" IPS chrome plated brass stay-open ball valve. Valve is US-made with chrome plated brass ball and Teflon® seals.
Pipe and Fittings: Schedule 40 galvanized steel. Furnished with orange polyethylene covers for vertical piping for high visibility and corrosion resistance.
Supply: 1¼" NPT female top or side inlet.
Waste: 1¼" NPT female outlet. Outlet tee can be positioned at either 8" or 20" above finished floor by reversing pipe nipples above and below lower tee.
Sign: Furnished with ANSI-compliant identification sign.
Contact us for order information for the following options only:
DC - Stainless steel dust cover for each spray head.
FC20 - Restricts shower flow rate to 20 GPM.
FC30 - Restricts shower flow rate to 30 GPM.
GRN - Green ABS plastic shower head.
YEL - Yellow ABS plastic shower head.
SSH - Stainless steel shower head.
Required by ANSI Z358.1-2004:
Unlike other mixing valves, the 08G3800 Thermostatic Mixing Valve is designed specifically for Emergency Shower Stations and precisely blends hot and cold water to deliver warm (tepid) water as required by ANSI Z358.1-2004.